Predictive vs. Preventive Maintenance – Which is Best?
Most facilities today have well thought-out maintenance programs. However, many facility managers are still asking one question: Which is better for my electrical system – preventive maintenance or predictive maintenance? In order to administer the best program, both preventive and predictive maintenance need to be incorporated. This often begs additional questions: Why should we continue to utilize older technology? Shouldn’t we jump on the new technology bandwagon and utilize only predictive maintenance?
It’s true that predictive maintenance is the wave of the future, and new technology will assist facility managers and business owners with making decisions around data. For example, alerts will be configured into analytical programs to notify users when particular assets are out of tolerance. When this happens, maintenance staff will have the ability to utilize all the data from the electrical system to best implement plans to remove assets or schedule downtime to maintain them. Either way, facilities will be able to shut down assets at a planned time, saving money and frustration for the maintenance staff.
You now may wonder: If we are able to schedule downtime with predictive maintenance, why would we still incorporate preventive maintenance into our plan?
Preventive maintenance still fits in many areas of an electrical system. While predictive maintenance is the wave of the future and will assist in increasing uptime, it will not work in every scenario. For example, every motor control center, starter panel, and smaller distribution panel board has critical equipment that it feeds. It may not make financial sense to install temperature sensors in all of these buckets, and the technology may not be available for each breaker. In these scenarios, performing preventive maintenance with a thermal imaging camera on a semi-annual or annual basis will give you the best protection against costly downtime. Preventive maintenance is also recommended for breakers and large fused switches. This equipment needs to be exercised on a yearly basis to ensure that the lubrication doesn’t become sticky, preventing the operation of the equipment. Trip units within the breakers also need to be tested on an annual or three-year basis depending on voltage and manufacturer.
At Faith Technologies, we see that best-in-class maintenance programs incorporate both predictive and preventive maintenance. Utilizing the best of both will create the highest levels of facility uptime.
< Back to Blog
If you enjoyed this blog article, please subscribe to stay up to date on the latest industry news from our experts at Faith Technologies.